Fire Shutter Door
High security commercial and service sites, up to 50m². These fire shutters have been tested at Exova Warringtonfire under BS EN 1634-1:2008 test conditions, and assessed to BS EN 476-22:1987, to contain fire within particular parts of a building for 1, 2 and 4 hours. All shutters can be connected to a fire alarm so they automatically descend by operation of the motor. Further fail-safe devices for higher levels of response to a fire outbreak or alarm are available. Suitable for internal or external face or reveal fit.
Requirements & Classifications
Electric, Tubular: Tubular motor with rocker or external key switch as standard and safety brake as appropriate to comply with legislation. Manual override facility and crank handle as required.
Electric, Outboard: Single phase inline chain driven motor (three phase option available) with push button control, chain override, fusible link and solenoid release as standard.